Payment & Shipping Terms:
|Model Name:||AL Power Cable||Size:||1.5~800 Sqmm|
600/1000V Compacted AL Conductor PVC Insulated and Sheathed Power Cable
Used outside as energy utility and lighting cables, in cable ducts, under ground, under normal
and salty water if specially made.
Conductor : Annealed Copper Conductor as per IEC 60228
≤6mm2 solid (class 1) or stranded (class 2)
＞6mm2 stranded (class 2)
Flexible conductor(class 5) optional.
Insulation : PVC rated at 90℃
Metallic Screen optional : Copper tape or copper wires braiding optional
Armored optional: : Aluminum wire or stainless steel tape for single core cable, Steel wire or steel
tape for multi core cable
Sheath : PVC or FR-PVC type ST2 to IEC 60502, black or red or customization
|Cu Core||Al Core|
|VV(VY);PVC(PE)sheathed power cable||VLV(VLY);PVC(PE)sheathed power cable|
|VV22(VV23);steel tape armoured,PVC(PE)sheathed power cable||VLV22(VLV23);steel tape armoured,PVC(PE)sheathed power cable|
|VV32(VV33),VV42(VV43);steel wire armoured ,PVC(PE)sheathed power cable||VLV32(VLV33),VLV42(VLV43);steel wire armoured ,PVC(PE)sheathed power cable|
Rated voltage: 0.6/1kV Low Voltage
Maximum Conductor Temperature: under normal (90 ℃), emergency (160℃) or short circuit no
more than 5 s (250℃) conditions.
Min. Ambient Temp. 0 OC, after installation and only when cable is in a fixed position
Min. Bending Radius: 20 x cable O.D for single core without armor
15 x cable O.D for multi core without armor
15 x cable O.D for single core with armor
12 x cable O.D for multi core with armor
ISO,CE, KEMA ,IEC, RoHS, CCC, P3C and more others at request
Number of Cores
Conductor Size & Construction
Type of Insulation
Armored or unarmored. If armour, the armour type & material
The Requirement of Sheath
Length of Cable & Packing Requirement
Packing and shipping
We are capable of meeting the most strict delivery schedules according to per purchase order.
Meeting the deadline is always the top priority as any delay in the delivery of cable can contribute
to overall project delay and cost overrun.
Cable is supplied in wooden reels, corrugated boxes and coils. Cable ends are sealed with BOPP
self adhesive tape and non-hygroscopic sealing caps to protect the cable ends from moisture.
The required marking shall be printed with a weather-proof material on the outsides of drum
according to customer's requirement.