Payment & Shipping Terms:
|Color Of Insulation:||Black Or As Per Order||Sample:||Freee|
|Rating Voltage:||600/1000V||Conductor Type:||Stranded Copper Conductor(class2)|
|Standard:||IEC 60502-1,UL1581||Main Market:||Asia,Midldle-East,African,|
Unarmoured CUnarmoured Copper Clad Aluminium Wire PVC / Polyolefin Sheathed YJVC-0.6/1KV
Copper clad aluminum wire and covered with welding manufacturing technology, high-quality copper cladding concentrically on the outer surface of the aluminum rod or steel wire core wire, and the formation of a strong metallurgical bond between the atoms between the copper layer and the core, so that two different metal materials combined into an integral whole, can make as drawing and annealing process as a single metal wire drawing process of copper and aluminum with adjustable proportion to the copper layer volume ratio remained relatively constant constant.
Copper clad aluminum conductor
XLPE or PVC insulation
PVC or polyolefin sheath sheath
Product Features Analysis:
1, DC resistivity: copper clad aluminum wire copper line resistivity large than about 1.5 times the copper wire, the female values are the same, copper clad aluminum wire copper wire weighs about 1/2.
2, The use of copper clad aluminum conductor can be continued for many years to meet the current in the wire and cable product selection, design, installation and other habits, also pressed the cable terminals, enabling soldering.
3, Lower AC resistance:
4, Light weight and low cost: Compared with the same technical specifications of copper cable, copper clad aluminum conductor cable cost savings of more than 40%, copper clad aluminum / copper composite conductor cable cost savings of more than 20%.
5, Good weldability: copper clad aluminum wire because of its surface coated with a layer of concentric copper, with copper wire so it has the same weldability, to facilitate the production
One is the signal or communication purposes copper clad aluminum cable, and the other is for power supply
Type and Data
0.6/1KV Single Core
|Nominal section of conductor||Nominal insulation thicknes (mm)||Thickness of sheath (mm)||
|20℃ Max DC resistance of conductor(Ω/KM)|
Contact Person: Mayling Zhao