Payment & Shipping Terms:
|Outer Sheath Material:||Copper||Rated Voltage:||600/1000V|
|Rated Working Voltage:||Light Load 500V Heavy Load 750V||Insulation Resistance:||≥ 10000 MΩ|
|Standard:||JG/T 313-2011||Rated Current:||Single-core 25-1800 A Multi-core 16-500 A|
|Outer Sheath:||Optional As Per Request|
High Temperature Resistant Cable,
High Temperature Electrical Cable
Heavy Load 750V High Temperature Electrical Cable With Strong Radiation Resistance
Structure of flexible fireproof cable
1. Cable conductor: it is made up of stranded copper wires, with favorable flexural property
2. Insulation layer : it adopts high-temperature resistant inorganic insulating materials
3. Copper sheath: copper materials, through special machining, with favorable flexural property. used as PE wire.
4. Outer sheath: it is made of plastic materials of low-smoke non-toxicity, with favorable corrosion protection.
Model of flexible fireproof cable
Y: series Symbol
T: Cooper conductor
T: Copper sheath
W: Inorganic insulation
. According to national standards, fire-resistant wire and cable: fire test method characteristic test, According to GB12666. 6 Class A, burn in fire with flame temperature 950℃ apply voltage of 750V between phase and phase and between phase and outer sheath it should be able to withstand for 90min without breakdown.
Class B, bun in fire with flame temperature 750-800 ° C, apply voltage of 750V between phase and phase and between phase and sheath it should be able to withstand for 90 min without breakdown.
2. According to the BS6378, flexible fireproof cable satisfies the following requirements:
Class A 650 ℃ 3h
Class B 750 ℃ 3h
Class C 950 ℃ 3h
Class S 950 ℃ 20min
1. Excellent fireproof property, the fireproof rating not only satisfies the national standard GB1266.6: category A 950 ℃ 90 min, hut also meet up with the U. K. standard BS 187-1994: Class A 650℃ 3h: class B 750℃ 3h; class C 950 ℃ 3h meanwhile, it also is able to withstand the water spraying or mechanical strike;
2. Long continuous length: the length can satisfy the length demand for power supply in spite of single-core or multi-core cable, and continuous length of each cable can be as long as 1000 m.
3. Large cross sectional area, sectional area of single-core cable reaches 630mm2 and that of multi-core cable reaches 70 mm2.
4. Property of flexibility, the cable can be wound on the cable reeI with the bending radius 6-10D, (D is the outer diameter of cable):
5. Smoke-free non-toxicity when burning, it adopts inorganic materials (non-inflammable materials) for insulation its burning would not produce any harmful gas or secondary
pollution it is an environmental protection product;
6. High overload capacity, the cable not only is high in current carrying capacity, but also has large overload capacity. According to the wiring requirements, the surf ace temperature of cable usually is 70 ℃ if it will not be touched or will not contact with flammable building materials the temperature of cable sheath can be heighten to 105 ℃. When coming across overload, long-term working temperature of fireproof cable can reach 250 ℃ ;
7. Property of corrosion proof, organic insulated fireproof requires plastic tube or tube or iron tube sometimes, the plastic tube is liable to deteriorate and iron tube is apt to rust or erode, but the fireproof cable has copper sheath and the tube is need-less, besides, copper sheath has favorable corrosion resistance.
8. Free of electromagnetic interference when wiring in the same vertical shaft with information wire and control wire because of shielding of copper sheath the fireproof cable would not interfere the single and control wires or cables ;
9. Tinguishing apparatus normally in flame, it reduces fire damage, extinguishing apparatus normally in flame, it reduces fire damage. Besides, it is reliable for personnel safety, as its copper sheath is a kind of good conductor, is the best earthed PE wire and covers the whole cable, the life of up to 100 years ;
10. Long service life, high-temperature resistance and degradation resistance of inorganic insulated material its service life is many times of that of organic insulated cables, under normal working conditions, its service Life can be as long as that of buildings;
11. Transportation and packaging of flexible fireproof cables including installation fittinos are simple nearly the same as that of general cables;
12. Favorable economical efficiency, due to advanced manufacturing processes and simple installation overall cost of flexible fireproof cable is much iower than that of mineral insulated cable under the same conditions.
Electrical characteristics of flexible fireproof cable
Manufacturing standards of flexible fireproof cable
|Nom. Cross-section of conductor||Strands No./Dia. Of Conductor||Nominal Insulation Thickness||Thickness of metallic sheath||O.D. of Cable
|mm2||pc/mm||mm||1 core||2 core||3 core||4 core||1 core||2 core||3 core||4 core|
|1 × 1.5||1/1.38||0.8||0.4||0.5||0.5||0.5||3.78||6.16||6.5||7.06|
|1 × 2.5||1/1.78||0.8||0.4||0.5||0.6||0.6||4.18||6.96||7.56||8.23|
|1 × 4||1/2.25||0.8||0.5||0.6||0.6||0.6||4.85||8.1||8.57||9.36|
|1 × 6||1/2.76||0.8||0.5||0.6||0.6||0.6||5.36||9.12||9.67||10.59|
|1 × 10||7/1.34||1.0||0.5||0.7||0.7||0.7||7.02||12.44||13.22||14.52|
|1 × 16||7/1.68||1.0||0.6||0.7||0.7||0.8||8.24||14.48||15.42||17.18|
|1 × 25||7/2.12||1.0||0.6||0.8||0.8||0.9||9.56||17.32||18.46||20.57|
|1 × 35||7/2.52||1.0||0.6||0.8||0.9||1||10.9||19.9||21.43||23.86|
|1 × 50||19/1.76||1.2||0.7||0.9||0.9||1||12.6||23||24.55||27.34|
|1 × 70||19/2.12||1.2||0.7||1||1||1||14.4||26.8||28.63||31.69|
|1 × 95||19/2.50||1.2||0.8||1||1||-||16.5||30.6||32.72||-|
|1 × 120||37/2.02||1.2||0.8||1||-||-||18.14||33.88||-||-|
|1 × 150||37/2.25||1.4||0.8||-||-||-||20.15||-||-||-|
|1 × 185||37/2.50||1.4||0.9||-||-||-||22.1||-||-||-|
|1 × 240||37/2.87||1.4||0.9||-||-||-||24.69||-||-||-|
|1 × 300||61/2.50||1.6||1||-||-||-||27.7||-||-||-|
|1 × 400||61/2.80||1.6||1||-||-||-||30.4||-||-||-|
|1 × 500||91/2.60||1.8||1.1||-||-||-||37.4||-||-||-|
|1 × 630||91/2.88||1.8||1.1||-||-||-||43.5||-||-||-|
|Nom. Cross-section of conductor||Strands No./Dia. Of Conductor||Conductor resistance Ω/km at 20 ℃ not more than||Calculation of resistance of copper sheath at 20 ℃(Ω/km)|
|mm2||pc/mm||Ω/km||1 core||2 core||3 core||4 core|
|1 × 1.5||1/1.38||12.1||4.19||2||1.89||1.73|
|1 × 2.5||1/1.78||7.41||3.75||1.75||1.36||1.24|
|1 × 4||1/2.25||4.61||2.61||1.26||1.18||1.08|
|1 × 6||1/2.76||3.08||2.33||1.11||1.04||0.945|
|1 × 10||7/1.34||1.83||1.74||0.689||0.646||0.586|
|1 × 16||7/1.68||1.15||1.19||0.587||0.55||0.432|
|1 × 25||7/2.12||0.727||1.05||0.429||0.401||0.32|
|1 × 35||7/2.52||0.524||0.935||0.377||0.341||0.28|
|1 × 50||19/1.76||0.387||0.68||0.285||0.266||0.215|
|1 × 70||19/2.12||0.268||0.591||0.22||0.205||0.185|
|1 × 95||19/2.50||0.193||0.451||0.191||0.179||-|
|1 × 120||37/2.02||0.153||0.408||0.172||-||-|
|1 × 150||37/2.25||0.124||0.366||-||-||-|
|1 × 185||37/2.50||0.0991||0.297||-||-||-|
|1 × 240||37/2.87||0.0754||0.263||-||-||-|
|1 × 300||61/2.50||0.0601||0.212||-||-||-|
|1 × 400||61/2.80||0.047||0.193||-||-||-|
|1 × 500||91/2.60||0.0366||0.149||-||-||-|
|1 × 630||91/2.88||0.0283||0.129||-||-||-|
We, Shanghai Shenghua Cable Group are specialized in R&D and manufacturing cables and wires. We have passed ISO9001:2008 International Quality System Certification(ZDHY), which covers the whole process of the management of the enterprise. A comprehensive quality control system has been put into place to ensure products meet international standards. Our tenet is: Set up top-ranking enterprise, high-class product, excellent service and well-known brand. "Abide by quality assurance, dedicated to provide users with reliable products always" is our commitment to quality. The products of our company are insured by PICC (the People's Insurance Company of China). Moreover, we offer specific guarantees as below:
1．We guarantee that we will comply with the requirements of warranty period specified in the contract.
2. We will be manufactured under this specification and that the Goods will be new, unused, of the most recent or current models. Once we are selected, we will supply the Goods strictly according to the requirements of the Contract.
3. The warranty shall remain valid for twelve (12) months after the Goods, or any portion
thereof as the case may be, have been delivered to and accepted at the final destination
indicated in the SCC, or for eighteen (18) months after the date of shipment from the port or
place of loading in the country of origin, whichever period concludes earlier.
4. During the warranty period purchaser may proclaim directly to the manufacturer in the written form or by the agent if there is any problem in Goods quality. The manufacturer will do the repair or replacement in reasonable time, and will bear all the expenses relating to this.
Shanghai Shenghua Cable (Group) Co., Ltd