2core 240mm2 Copper Conductor XLPE Insulated Power Cable Armored or Unarmoured 0.6/1KV Electric Cable
Applications: XLPE Insulated Cable is used as power distribution and transmission line at rated voltage 0.6/1KV.
|Conductor||Copper Conductor as per IEC 60228,Class 2|
|Circular or Shaped conductor|
|Flexible conductor(class 5) optional.|
|Insulation||XLPE (Cross-Linked Polyethylene) rated at 90℃,many color optional|
|Metallic Screen optional||Copper tape or copper wires braiding optional|
|Sheath||PVC or FR-PVC type ST2 to IEC 60502, black or red or customization|
Technical data: Rated voltage:0.6/1kV Low Voltage
Maximum Conductor Temperature: under normal (90℃), emergency (130℃) or short circuit no more than 5 s (250℃) conditions.
Min. Ambient Temp. 0 OC, after installation and only when cable is in a fixed position
Min. Bending Radius: 20 x cable O.D for single core without armor
15 x cable O.D for multi core without armor
15 x cable O.D for single core with armor
12 x cable O.D for multi core with armor
Standards: International: IEC 60502, IEC 60228, (IEC 60332-3 for FR-type only)
China: GB/T 12706, (GB/T 18380-3 for FR-type only)
Other standards such as BS, DIN, VDE and ICEA upon request
1. The installation temperature should not over 20℃, If the ambient temperature is lower than 0℃, the cable should be preheated.
2. The bending radius of cable should not less than 8 times.
3. After installation, the cable should with stand voltage test for 15min. 3.5kv D.C.
|Nom. Cross-section of conductor||Insulation Thickness||Sheath Thickness||Approx. O.D.||Approx.Weight||Max. D.C Resistance of Conductor (20 ℃)||Testing Voltage A.C||Current Rating|
|mm2||mm||mm||(mm)||kg/km||Ω /km||kV/5min||In air (A)||In soil(A)|
|1 × 240||1.7||1.7||25.0||2510||0.0754||3.5||535||540|
|3 × 240||1.7||2.4||46.0||7243||0.0754||3.5||440||450|
|4 × 240||1.7||2.5||47||9836||0.0754||3.5||440||450|
|5 × 240||1.7||3.0||64.0||13130||0.0754||3.5||440||450|
|3 × 240+ 1 × 120||1.7||2.5||48||8501||0.0754||3.5||440||450|
|4 × 240+ 1 × 120||1.7||2.7||54.2||11567||0.0754||3.5||440||450|
Application Standard: IEC/BS/UL/GB
Number of Cores
Conductor Size & Construction
Type of Insulation
Armored or unarmored. If armor, the armor type & material
The Requirement of Sheath
Length of Cable & Packing Requirement
Packing and shipping: We are capable of meeting the strictest delivery schedules according to per purchase order. Meeting the deadline is always the top priority as any delay in the delivery of cable can contribute to overall project delay and cost overrun.
Cable is supplied in wooden reels, corrugated boxes and coils. Cable ends are sealed with BOPP self-adhesive tape and non-hygroscopic sealing caps to protect the cable ends from moisture. The required marking shall be printed with a weather-proof material on the outsides of drum according to customer's requirement.
We, Shanghai Shenghua Cable Group are specialized in R&D and manufacturing cables and wires. We have passed ISO9001:2008 International Quality System Certification(ZDHY), which covers the whole process of the management of the enterprise. A comprehensive quality control system has been put into place to ensure products meet international standards. Our tenet is: Set up top-ranking enterprise, high-class product, excellent service and well-known brand. "Abide by quality assurance, dedicated to provide users with reliable products always" is our commitment to quality. The products of our company are insured by PICC (the People's Insurance Company of China). Moreover, we offer specific guarantees as below:
1．We guarantee that we will comply with the requirements of warranty period specified in the contract.
2. We will be manufactured under this specification and that the Goods will be new, unused, of the most recent or current models. Once we are selected, we will supply the Goods strictly according to the requirements of the Contract.
3. The warranty shall remain valid for twelve (12) months after the Goods, or any portion
thereof as the case may be, have been delivered to and accepted at the final destination
indicated in the SCC, or for eighteen (18) months after the date of shipment from the port or
place of loading in the country of origin, whichever period concludes earlier.
4. During the warranty period purchaser may proclaim directly to the manufacturer in the written form or by the agent if there is any problem in Goods quality. The manufacturer will do the repair or replacement in reasonable time, and will bear all the expenses relating to this.
Shanghai Shenghua Cable (Group) Co., Ltd