Payment & Shipping Terms:
|Wrapping Tape:||LSOH BendingTape||Sheath:||LSOH Flame Retardant|
|Rated Voltage:||600/1000V||Cores No.:||5 Cores|
fire retardant cable,
fire proof cable
Fire Resistant XLPE insulation Flame Retardant sheath Power cable
To be laid directly in ground, outdoors, indoors and in cable ducts.
Used for tall building, Hospital, Theatre, Power station, Metro Tunnel or Petrochemical Industry or other special place required for low smoke , zero halogen clean and safe cable.
1,Long-term allowable operating temperature of cable conductor ≤90°C
2Highest working temperature of cable in case of short circuit (the longest lasting time is not over 5s): cable conductor≤ 250°C
3The laying temperature should over 0℃,Permissible bending radius of cable:for single core unarmored cable, should be no less than 20 times of it’s outer diameter ; for multi-core unarmored cable, should be no less than 15 times of it’s outer diameter
4,With fire-resistant property, N,ZAN,ZBN,ZCN,ZDN are 5 types
5The product is applicable for AC 50 Hz transmission and distribution lines with rated voltage of 0.6/1KV
1 ..... stranded (RM) bare copper
2 ..... Mica Tape for Fire Resistant
3 ..... core insulation of cross-linked polyethylene
4 ..... Fillers
5 ..... Wrapping tape or Flame Retardant tape
6 ..... PVC Inner Bedding
7 ..... Galvanized Steel Wire Armour
8 ..... outer sheath of polyvinylchloride (PVC)
IEC 60502, 60228, 60332, 60331
DIN VDE 0276-620
HD 620 S1: 1996
DIN EN 60228 class 2 (construction)
Test voltage 0.6/1 kV [kV] 3.5 / 5 min.
Temperature range in motion -5°C till +70°C
fixed -20°C till +70°C
Operating temperature short circuit °C 250
Short circuit time max. [sec] 5
Bending radius min. x diameter 15
Flammability standard EN 60332-1-2
lnternational: IEC60502. IEC60228, (lEC60332-3forFRcableonly) China: GB/T12706,(GB/T18380-3 for FR cable only)
Other standards such as BS, DIN and lCEAupon request
Rated voltage: 0.6/ 1㎸
Maximum Conductor Temperature: under normal (90°C), emergency(130°C) or short circuit no more than 5 s(250°C) conditions Min.Ambient Temp.-15°C,lnstallationTemp.0°C
The maximum rated temperature
XLPE insulated,the maximum operating temperature of conductor shall exceed 90℃when the cable is used for long not period. The temperature of conductor shall not exceed 250℃ at short circuit for 5 seconds.
PVC insulated,the maximum operating temperature of conductor shall exceed 90℃ or 70 ℃ when the cable is used for long not period. PVC insulated the temperature of conductor shall not exceed 160℃ at short circuit for 5 seconds.
The installation of cable is not limited by the difference of elevation along the route. The ambient temperature should not be below 0℃ during installation. The permissible bending radius for cable shall be complied with the following regulations:
For single-core: R>20(D+d) +/-5%
For multi-core: R>15(D+d) +/-5%
Where:R—bending radius (mm) , D—overall diameter of the cable (mm) , d—diameter of conductor (mm).
Single core cable of using in AC circuit shall be without armour or with steel wire armour and shall not be laid in magnetic ducs.