Payment & Shipping Terms:
|Name:||XLPE Electrical Cable||Conductor:||Copper Conductor, Cl.2 As Per IEC 60228|
|Conductor Screen:||Semi-conductor||Insulation:||XLPE Insulation (cross-linked Polyethylene) Rated At 90 OC|
|Insulation Screen:||Semi-conductor||Screen:||Copper Tape|
|Sheath:||PVC Or FR-PVC Type ST2 To IEC 60502, Black||Core:||Three Core|
33kV xlpe armoured cable,
Copper 3 Core xlpe cable
33kV Three Core Copper Conductor XLPE Insulated Medium Voltage Power Cable
Medium Voltage Power Cable Construction
Conductor : Compact Stranded Copper Conductor, Cl.2 as per IEC 60228
Conductor Screen: Semi-conductor
Insulation : XLPE insulation (cross-linked polyethylene) rated at 90 OC
Insulation Screen: Semi-conductor
Screen : Copper tape
Sheath : PVC or FR-PVC type ST2 to IEC 60502, black
Medium Voltage Power Cable Applications
The medium voltage cable can be choosed for laying indoors and outdoors. Able to bear certain traction during installation, but not external mechanical forces. Laying single core cable in magnetic ducts is not allowed.
Medium Voltage Power Cable Standards
International: IEC 60502-2, IEC 60228,
China: GB/T 12706, (GB/T 18380-3 for ZR-YJV only)
Other standards such as BS,DIN and ICEA upon request
Medium Voltage Power Cable Technical data
Rated voltage: 19/33kV
Maximum Conductor Temperature: under normal (90 OC), emergency (130OC) or short circuit no more than 5 s (250℃) conditions.
Min. Ambient Temp. 0 OC, after installation and only when cable is in a fixed position
Min. Bending Radius: 20 x cable O.D for single core
15 x cable O.D for multi core
Medium Voltage Power Cable Certificates
CE, RoHS, KEMA and more others at request
Commercial Items: FOB Shanghai Port or CIF port as per request. MOQ: 800m
Payment terms: 30% T/T before production, 70% T/T before delivery
Packing: Wooden Iron drum, whole steel wooden drum if required by client side.
Medium Voltage Power Cable Specifications
|Nom. Cross-section of conductor||Strands No./Dia. Of Conductor||Insulation Thickness||Sheath Thickness||Approx. O.D.||
|Max. D.C Resistance of Copper Conductor (20 ℃)||Testing Voltage A.C||Current Rating|
|mm2||pc/mm||mm||mm||(mm)||kg/km||Ω /km||kV/5min||In air (A)||In soil(A)|
|3 × 50||10/2.52||10.5||3.5||78.6||5491||0.387||91||180||190|
|3 × 70||14/2.52||10.5||3.6||82.3||6649||0.268||91||220||230|
|3 × 95||19/2.52||10.5||3.7||85.9||7744||0.193||91||265||275|
|3 × 120||24/2.52||10.5||3.8||89.2||8833||0.153||91||305||315|
|3 × 150||30/2.52||10.5||3.9||92.8||10008||0.124||91||345||355|
|3 × 185||37/2.52||10.5||4.0||96.5||11381||0.0991||91||390||400|
|3 × 240||48/2.52||10.5||4.2||101.6||13408||0.0754||91||455||460|
|3 × 300||61/2.52||10.5||4.3||106.6||15520||.0601||91||525||520|
|3 × 400||61/2.97||10.5||4.6||114.1||18942||0.047||91||600||590|
Q1. Are you a factory or trading company?
We are factory in Hebei,China.
Q2. When can I get quotation for cable?
We usually quote within two hours after we received your inquiry. If you are urgent to get the unit price, please let me know. We can quote it ASAP.
Q3. How can I get the sample to check the quality?
When you confirm the quotation, we can offer you the sample for free. You just need to pay the freight.
Q4. What about the lead time for mass production?
It depends on your order quantity. If we have stock, 5 days is OK. If custom products, usually it's need 12 days.
Q5. Do you have OEM products?
Sure, we can make cables as you want. We can change the color and logo on cable as you want.